I had a very bizarre electrical event after a recent windstorm and outage. I will describe the resulting problem first and then describe the event after.
A two glass fuse use block (these are old design) blew on my electrical panel during or after a power outage. Each glass fuse 20 amp. Each of these glass fuses seemed really BLOWN compared to blown fuses I have seen in the past. And the contact on one side was scorched. I have attached photos.
If I now turn the power off to the main panel, remove this two fuse block, insert two new glass fuses, turn the power on, the two fuses will blow. Note: I have checked this circuit which is for an electrical outlet and could see nothing amiss. The presumption then is that the problem with this two fuse block is a result of the power outage itself rather than the circuit involved since that circuit was fine before the outage.
So, my question is: can this two fuse block itself blow or be defective over and above the two glass fuses themselves? In other words, if I turn the power off, put two 20 amp fuses into a new two fuse block, insert that block and turn the power on, will all be OK?
This bizarre event occurred in this fashion:
There was a windstorm and power outage in the morning. The power came back on about 11AM. I went to town and on the way back I saw some power trucks in the neighborhood and assumed the power would be out when I got home. Sure enough the power was out.
I waited for the power to come back on and at dark noted that a street light was on above my house. I walked down below my house and a street light was on. I went to my neighbors' house across the way and she said the POWER HAD BEEN ON ALL DAY!!
But my power was out. This made no sense to me at all. I thought on this a while. I thought I should exhaust all possible remedies first, so I went in the basement, turned off the power to my main panel and turned it back on. THE POWER CAME ON!
This makes absolutely no sense to me. Anyway, the next morning I thought I should inspect the panel. I shut the power off and in examining it, found the above problem with the two fuse block. I put in two new fuses, turned the power on and the fuses blew as described above.
So, my second question is: what is the explanation for this, to me (electrical non-expert) bizarre event? ( I have told this story to a few people and they are mystified.)
The larger message may be to turn off your main entry panel during an outage. Of course, how do you know when the power is back on?
Peter Kelly wrote:..... The presumption then is that the problem with this two fuse block is a result of the power outage itself rather than the circuit involved since that circuit was fine before the outage.......
I noticed that you say you checked the circuit but didn't notice anything. What is on the circuit connected to the glass fuses??? I suggest that you remove all items plugged into the circuit connected to the glass fuses entirely: often times a device can go faulty suddenly and the device will start draw more amps the fuses can handle without appearing to be visually different in any way.
Yes, the block itself can go bad, but you won't know that until you've removed every single item on the circuit, plugged in two new glass fuses, and turned the power back on.
The second question is unanswerable. I've never believed in occam's razor as I've seen results from events that have many simple explanations which are not the actual real explanation. It turns out life is stranger than fiction and the chance of the real explanation being simple seems to be about 50%. Make up your own story until someone can prove it wrong, you can think of a counter example to disprove it, or someone tells you why logically this cannot be true.
I have had this problem, but in my case it ended up being a grounding issue. I am not sure that is the case with you though.
We know a few things, and that there was not an issue with your place until there was a storm in the area. Since power trucks were on your road, we can also conclude that there was damage done on your road. Now why your neighbor was not affected, and you were, could take the shape of many things. Some of it depends on whether the area lines are 3 phase or single phase, but also where the circuit breaker/breakers is for the main power line for your street.
There are a few possible results here:
1. The storm did damage directly to the circuit/circuits in question
2. When the power came back on it did damage to the circuit/circuits in question
3. There was damage done to the grounding of the electrical system somewhere on the home
4. The fuse box itself is damaged
By the way I read and reread your post, it seems the two fuses that keep blowing, are feeding a single 220 volt circuit. Is that correct?
1. To blow a fuse repeatedly means there is too much amperage in the circuit somewhere. That could take on the form of water getting in on the wiring somehow, so it may be subtle, or in an area where you cannot see the wires. You said you had a storm, but what was it like? High winds only or high winds with heavy rain?
2. You have fuses which tells me the entire wiring system is rather old. Copper gets really brittle as it ages, so it is possible that when the power was returned by the power company, the sudden amp draw did damage to that particular circuit.
3. This scenario ties in with number two, but I have seen some really goofy grounding methods in my life. If someone tied the neutral to the ground somewhere, and that is most likely the case with older wiring, goofy things can happen.
4. Again, either when the storm hit, or afterwards when the power came back on, damage was done to the fuse box, again a rather old electrical component.
Just because power did not go out in your neighbor's house, does not mean it did not go out in yours. I had a high wind storm one year pull the wires right out of my meter box. I was without power for 9 days, whereas my neighbors had theirs on the whole time. It also broke the components inside the meter box.
You could call your power company and find out what occurred on your street. I am not sure that it would matter because I think you are going to need an electrician. All it takes is brittle copper to break a connection somewhere and it will overenergize the circuit and cause it to blow the fuses. That is hard to diagnose online.