My family recently purchased a business in Maine. The building is about 3000 sq ft and is heated with a Sequoia Paradise wood furnace. I am able to fit a 55g drum inside the furnace and we were thinking of fabricating a feed/air tube at the opening of the door. Will a rocket mass heater produce enough heat for our system which circulates 210 gallons of water? When the furnace is filled and running efficiently it brings the water temp to 180. Can a rocket mass heater be designed in a closed area? Here are the specs for our furnace:
Paradise model E3400 outdoor wood furnace. It
has a 320,000 Btu/hr rating, with a forced
downdraft gasification design. The firebox is 44"
deep x 48" tall x 32" wide, holding 39 cubic feet
of fuel. The unit stands 60" wide x 72" long x
If its a gasification boiler efficiency wise you are head and shoulders above what standard wood boilers can achieve already. I think controlling your usage will result in better results then modification. It will work far better with dry wood which should be obvious but many people used to the old outdoor furnaces that " can burn anything" will try to burn anything in an efficient unit and have horrible results. Matching your call for heat to the intensity of the fire will go a long way to increasing efficiency as well. Also those gasification boilers are most efficient at full load so if there is any way you can incorporate in home storage that would be a good thing to do. The simmer, heat up, simmer heat up common in forced air linked systems is what kills your efficiency numbers...
Top of head... Cheers, David
Location: Southern alps, on the French side of the french /italian border 5000ft elevation
posted 2 years ago
Well, how high from the ground is your door?
How wide and tall is it?
I think i would try a huge batch, with the heat riser entering that door.
You might have to do a broken riser. May be you Can fit a 12 or 14 inch batch.
How strong is your draft?
The other thing, you most certainly will have to make a plunger tube, to use the boiler as a bell.
I think it's time to gather firebricks, tubes, and superwool.
I forgot. You might well have to build another bell, since you internal surface area will be too small. And a good idea, would be to build it around the boiler, to heat inside and out. Tho, you will loose heat to the outside surface of the bell.